Designing the electrical system and installing the conduit for future PV was ideal. When PV was added, it was installed in a few hours. The photovoltaic system and inverter are used for an uninterruptible power supply (UPS) system. A better definition of what loads were to be UPS-powered would have been useful, however. The UPS system is not guaranteed to provide continuous power. About 5 percent of the outgates have left the building with a brief (less than 1 second) outage—enough to reset computers. Some small UPS computer backups have been installed for the brief outages.
Cool-towers have worked as well as direct evaporative coolers except in the enclosed offices, where additional small fans were added. The recommendation is that cool-towers be used only in large open spaces.
Daylighting levels have been lower than anticipated. This was due to the large number of dark beams in the space and the white stained ceilings (instead of white paint, as modeled). In addition, bug screens on the operable windows have affected the daylighting level. The result has been additional operation of artificial lighting.
Trombe walls have exceeded operational expectations. However, a design change resulted in two enclosed offices against Trombe walls, and these offices tend to overheat. In large open zones, the Trombe walls are very effective.
Was this article helpful?
Do we really want the one thing that gives us its resources unconditionally to suffer even more than it is suffering now? Nature, is a part of our being from the earliest human days. We respect Nature and it gives us its bounty, but in the recent past greedy money hungry corporations have made us all so destructive, so wasteful.