The grit in wastewater has a specific gravity in the range of 1.5-2.7. The organic matter in wastewater has a specific gravity around 1.02. Therefore, differential sedimentation is a successful mechanism for separating grit from organic matter. Also, grit exhibits discrete settling, whereas organic matters settle as flocculant solids (see Section 7.21).
The velocity-controlled grit channel is a long, narrow, sedimentation basin with better flow control through velocity. Some wastewater treatment plants control the velocity by using multiple channels. A more economical arrangement and better velocity control is achieved by the use of control sections on the downstream of the channel. These control sections maintain constant velocity in the channel for a range of flows by using proportional weirs, Parshall flumes, and parabolic flumes.
To design effective grit removal facilities, environmental engineers must know the volume of the sewage flow and quantity of grit. The quantity of grit can be variable; therefore, a safety factor must be allowed. Multiple channels are usually provided when manual grit cleaning is used.
The typical values of detention time, horizontal velocity, and settling velocity for a 65-mesh (0.21-mm diameter) material are 60 sec 0.3 m/sec, and 1.15 m/min, respectively. The theoretical length is 18 m (60 ft). The depth of flow is governed by the volume of sewage flow. The width is not critical but is normally small so that the channels are long and narrow.
The head loss through a velocity-controlled channel is 30-40% of the maximum water depth in the channel. The effect of scouring the settled grit surface at this velocity washes away much of the putrescible material that settles out with the grit. The grit removed by this design usually requires burial to prevent odor.
Grit chambers can be cleaned manually or mechanically. Manual cleaning is usually used only in smaller and older plants where manual methods are used to rake, shovel, or bucket the grit from the chamber. During this operation, flow to the chamber is shut off or diverted to another channel, and the grit tank is drained for cleaning. Designing the grit chamber with the necessary depth provides grit storage.
Mechanical grit removal equipment consists of moving bucket scrapers, horizontal and circular moving rake scrapers, or screw conveyors. Once the grit is removed from the grit collection tank the facility dewaters it using screw or rake classifiers, screens, or similar devices. Hydraulic ejectors, jets, and air lift pumps are also used. Mechanically cleaned tanks require a smaller grit storage volume. Aeration is occasionally used in the grit chamber to wash out organic material from the grit. Figure 7.15.1 shows a mechanical grit removal design.
FIG. 7.15.1 Mechanical grit removal facility. A. Plan view; B. Longitudinal section.
Was this article helpful?